Here are the results of an E-Tubes System installation in a typical convenience store:
Installation: Installed 200 linear feet of E Tubes in primary Beverage Cooler.
Dimensions of Cooler: 56’ L x 14’ W x 8’ H.
Heat Intrusion Challenges: Twenty (20) glass doors, and deliveries of 100+ cases of room-temperature beer several times per week.
|Cooler Compressor Run Times:||23 hrs./day||
8 to 9 hrs./day
|Product Temperatures:||33.60 F average||
29.68 F average
Eliminated the need for one of 3 compressors; now using 2 compressors rather than 3.
#1 compressor run time reduced by 44%
# 2 compressor run time reduced by 69%
# 3 compressor run time reduced by 100%
Reduced the Average Product Temperature by 3.92 Degrees F.
Reduced Humidity in Cooler. Cooling Equipment Runs More Efficiently.
Our Installation Procedure
Coordinate with remodels where possible
Minimize disruption to store operations
Maximize installation efficiency
Use licensed installation professionals
Provide warranty and rapid support
Customize installations based on store format
Provide pre-installation and post-installation data analysis
Coordinate with government agencies and utilities to procure energy rebates
Benefits to your Stores
- Profit Margin Increase
- Immediate Energy Savings
- Swift ROI
- Limit Exposure to Energy/Water Price Volatility
- Reduce your Carbon Footprint
- Compliance with Internal & External Initiatives
- Public Relations/Brand Management
- Improved Reputation and Leadership